Steam Turbine Generators Condensing
Used Dresser-Rand frame S-6, 2500 kw single valve multi stage condensing steam turbine, 6000 rpm, inlet steam 200 to 300 psig, 500 to 600 deg f, exhaust 2”hga, CW rotation looking from governor end, 1 curtis 6 rateau stages, 6” class 600 inlet size, 30” class 125 up exhaust. Ideal 2941 kva, 2500 kw, 4160 v, 3 phase, 60 hz. Air cooled with brushless exciter. 1800 rpm. Graham surface condenser, 3271 sq. ft, 43,000 lbs/hr steam condensed. Hand valve for part load operation. Lube oil system, gland steam condenser. SCOPE OF SUPPLY: Steam turbine, gear reducer, generator, trip and throttle valve, lube oil system mounted on common skid Condenser, air ejector, condensate extraction pumps with motor Generator terminal box with surge protection system, ct’s, pt’s Local turbine gauge board. Neutral ground resister Manuals and drawings
Location: South USA
Used 10.5 megawatt condensing turbogenerator set made by AEG-Kanis (Germany). Steam parameters: inlet steam flow 50.4 ton/hour. Inlet stem pressure 18 bar. Inlet steam temperature 350 degrees Celsius. Outlet steam flow 50.4 ton/hour. Outlet stem pressure 0.095 bar. Outlet steam temperature 44.8 degrees Celsius. Speed of the turbine 7100 rpm. Generator made by Voith with following parameters - 11215 kW, 50HZ, 11000 V. 1500 rpm. Condenser made by GEA 2815 M3/hour.
Used power plant with 120 tph of steam at 62 ATI at 430C temperature and 11mw ABB / CKD condensing turbogenerator. New 2015 (4) burners for gas and fuel oil. Used to work with 1500 tpd sugar refinery from raw sugar.
Used biomass-coal power plant with the capacity 1500kW (1.5MW). Main equipment: Turbogenerator set by Kaluga П-1,5-21/5, steam consumption 10t, inlet pressure 21 bar, bleed steam outlet pressure 5 bar, operation time 10000 hours. Water tube boiler, 12.5t of steam per hour, 23bar, 350*C, operation time 11000 hours. Fuel coal and wooden chips (70%-30%). Reported that Boiler can opperate on 100% woodchips after modernisation. Additional information on request.
25 MW Westinghouse Steam turbine generator. Inlet pressure: 59.76 kg / cm2 (850 psi), inlet temperature: 482.2° Celsius. (900° Fahrenheit) rpm 3600, stages 13, model: YD1, 13.800/296V, 250 kVA dry generator, 1972. Generator manufacturer: Westinghouse model 500886 power 25 MW nominal tension 13.800 KV - 60Hz - rpm 3600 manufacture date: 1972. Condenser not included.
Location: SOUTH AMERICA
Used 3,000 kW Triveni (India) Steam Turbine Generator Set, new in 2007. Consisting of: - Triveni (India) extraction-condensing steam turbine, new in 2007, has capacity 3,000 kW, inlet steam flow 19200 kg/hour at steam pressure 65 ata @ 485 Deg.C., extraction flow 8000 kg/hour at pressure 8/10 ata, Includes Teil model HSG-432 gearbox, single helical type, input speed 8325 rpm, output speed 1500 rpm, - TDPS alternator, capacity 3750 kVA voltage 11000V 3phases 50Hz, - Alternator cooler, condenser with condensate extraction pumps, oils pumps, actuators, accumulater, control oil firlter, couplings Exclusions: Cables, Oil Coolers, Oil Filters & Electrical Panels are not available. More details upon request.
Used General Electric turbogenerators #1 with backpressure 5,000 kW to 4160V each. These turbines operate nominally 415 psig steam to 715ºF, and 400 psig to 625ºF with vapor pressures of 35 psig and exhaust 10 psig. respectively.
Used General Electric turbogenerators #2 with backpressure 5,000 kW to 4160V each. These turbines operate nominally 415 psig steam to 715ºF, and 400 psig to 625ºF with vapor pressures of 35 psig and exhaust 10 psig. respectively.
Used biomass cogeneration plant with electric capacity 5 MW or 5000 KW. Two Boilers with steam parameters: 45 bar, 420°C, 25 t/h (2x12.5 t/h). Fuel type: Wood chips with the moisture content above 50%. Condensing Steam turbo generator electrical output: 5 MW (MAN-Turbo). Turbine is equipped with extraction: 2.4 bar (0 -20 t/h). Air Cooled Condenser. Generator: 6.250 kVA, 6.3 kV, 50 Hz – Schorch/LDW. Emission cleaning system parameters comply with EU standards. Fuel preparation and feeding system is included as well as control room, cyclones and other auxiliary equipment. Plant has been started in 2000, operated until 2014. More information on request.
Used 6,000 kW Belliss (India) Steam Turbine Generator Set, new in 2000. Consisting of: - Belliss India Ltd (India) model HEN-22 extraction condensing steam turbine, new in 2000, has capacity 6,000 kW, inlet steam pressure 44 kg/cm2 @ 420 Deg.C., with extraction/bleed capacity 11 tph at pressure 7 kg/cm2. Includes Triveni Engeneering Ltd (Mysore) gearbox, coupled on common baseframe, input speed 8600 rpm and rate 5.76/1 which gives output speed 1500 rpm, - Toyo Denki Japan – by Kirloskar Elec. Co. Ltd alternator, new in 2000, voltage 11000V, air cooled by cooling tower water circulation. More details upon request.
Used 6,000 kW Triveni (India) Steam Turbine Generator Set, new in 2002. Consisting of: - Triveni Engineering & Industries Ltd. (Bangalore-India) model FR13 condensing steam turbine, new in 2002, has capacity 6,000 kW, inlet steam pressure 63 kg/cm2 @ 480 Deg.C., includes Triveni Gears (Mysore) model HSG-560 gearbox, coupled on common baseframe, input speed 8312 rpm and rate 5.54/1 which gives output speed 1500 rpm, - VA Tech alternator, capacity 7500 kVA voltage 11000V 3phases 50Hz, mounted on baseframe, - Governing System for Turbine, - Oil Cooling System including Oil Filters, AOP with Motor, MOP mounted on gearbox shaft, oil tank, etc. - Radiators for Alternator Cooling, - Excitor and control panels for turbine, alternator, AVR panel. Condensing System, Oil Cooler, Cables & VCB Panel are not included. Reportedly slightly used. More details upon request.
Manufacturer: Dresser-Rand Type RD6M2 Steam Turbine rating: 6600 kW inlet steam: 600 PSIG/750 deg F exhaust steam: 3"HGA steam rate: 10.38 lbs/KWH speed: 5361 rpm turbine rotation: CW (view from governor end) gear reducer: manufacturer: Lufkin rating: 9215 HP speed: 5361/1800 rpm manufacturer: GEC Alsthom rating: 7765 kVA voltage: 6900 V/3 phase, 60 Hz, 0.85 pf type: air cooled scope of supply: steam turbine with gear reducer mounted on one skid generator with brushless exciter turbine inlet trip valve air cooled condenser designed for 58,260 lbs/hr turbine control panel generator control panel Woodward 505 governor panel Lube oil system spare parts, manuals and drawings year built 1995 shutdown 2011
Turbine: Manufacturer/Type: Mitsubishi Type Sc1f - 29.5” Ax, Single Cylinder, Axial Exhaust Output: 80,000 Kw Inlet Steam: 1500 Psig/970 °F Induction Steam: 90 Psig/400 °F Exhaust Steam: 2” Hga Number of Stages: 12 Speed: 3600 Rpm Generator: Manufacturer/Type: Mitsubishi Type Mb Rating: 94118 Kva, 13800 V, 0.85 Pf, 3 Phase, 60 Hz Speed: 3600 Rpm Rotation: Ccw From Drive End Scope of Supply: Steam Turbine, Generator, Trip And Throttle Valve, Lube Oil System, Condenser, Air Ejector, Condensate Extraction Pumps with Motor Generator Terminal Box With Surge Protection System, Ct’s, Pt’s Manuals And Drawings History Unit Built 2001 Part of Combined Cycle Power Plant.
Location: Midwest USA
Used Siemens steam turbine model EK8002. (2) 4000 kW, 8000 rpm, 42 kg/square centimeter. 10/11 kg/square centimeter 1st extraction; 6/7 kg/square centimeter 2ND extraction. Consisting of: (2) electrical generators with (2) boilers to produce 4MW plus 40 tons/hour of steam @ 100 PSIG each, consisting of the following equipment: - (2) 40 tons/hour steam boilers manufactured by Cerrey (combustion Engineering in Mexico), type 30VPI12M, series 7721 and 7722, 50.3 kg/sq. Cm. - (2) centrifugal blowers, 400 HP and 300,000 cu. M. Of air; (2) Viking 5 HP fuel oil, 1200 rpm pumps; (2) 7 sq. M. Shell and tube type fuel oil heaters; (2) fuel oil gear pumps for ambient temperature, 3 HP, 1750 rpm; (1) carbon steel caustic soda tank; (1) carbon steel sulfuric acid tank. - water treatment system (demineralize) with: (1) 6.5 cu. M. Cation tank (Zeolites; (1) 120 cu. M./hour gas release tower with PVC Rashing ring packing; (1) 2.5 cu. M. Anion tank (Zeolites; 25 HP pump for tower and 3 HP fan for tower. - (4) high pressure water pumps manufactured by Zulzer, (3) small carbon steel flash tanks, and (2) small centrifugal pumps for flash tanks. - (2) Siemens 4000 kW steam turbines type EK8002, 8000 rpm, 42 kg/sq. Cm steam input, 1st extraction: 10/11 kg/sq. Cm., 2ND extraction 6/7 kg/sq. Cm. - all auxiliary equipment such as vacuum pumps, control panels, fan for cooling control pane, and air handling unit for turbine room. - (2) Siemens 60 Hz, 6600 volt electrical generators.
Steam turbine: manufacturer: Murray (Dresser-Rand) rating: 9500 kW rating with zero extraction: 6500 kW inlet steam: 850 PSIG/750 deg F extraction steam: 125 PSIG extraction steam flow: 0 to 50,000 lb/hr maximum inlet steam flow: 120,000 lbs/hr maximum exhaust flow: 75,000 lbs/hr number of stages: 9 speed: 4711 rpm inlet steam flange: 6" side exhaust flange: 48" top control: Woodward 505E gear reducer Lufkin 4700 to 1800 rpm generator: manufacturer: ideal rating: 11177 kVA kW: 9500 pf: 0.85 type: Tewac exciter: brushless 25 kW. Year built: 2001 last year run: 2008 scope of supply steam turbine generator skid Lube oil system, condenser, air ejector and turbine control panel. Excluded: cooling tower, gen control panel and breakers
Manufacturer: TGM WEG Energia model CTE40 Steam Turbine Generator Type: Condensing Rating: 30,366 kw Inlet Steam: 1500 psig/1000 °F Exhaust Steam 2.8“ hga Maximum Inlet Steam Flow: 275,578 lbs/hr Steam Rate: 9.08 lbs/kwh Extraction Steam 4 Uncontrolled and 1 Controlled Extraction 40 psig (0 to 255,00 ls/hr) Inlet Steam Size: 10” Extraction Steam 24” Speed: 6000 rpm Rotation: CW from Governor End GEAR REDUCER: Manufacturer: TGM WEG Energia Input Speed: 6000 rpm Output Speed: 1800 rpm Rating: 37,047 kw Service Factor: 1.3 GENERATOR: Manufacture/Type: TGM WEG Energia TEWAC Model: ST41 Rating: 46,167 kva, 13800 v, 3 Phase, 60 hz Field: 125 v dc, 4.5 amps PF: 0.8 Exciter: PMG , Brushless Type Speed: 1800 RPM CONDENSER: Type: Water Cooled Horizontal Steam Condensed: 240,000 lbs/hr Cooling Water Flow: 31,630 gpm @ 95 °F Tubes: Stainless Steel SCOPE OF SUPPLY Steam Turbine Mounted on Skid, Gear Reducer, Generator with Terminal Box and Exciter Inlet Stop Valve Lube Oil System with Lube Oil Tank, Lube Oil Cooler, Pumps Gland Steam Condenser Turbine Control Panel with PLC Control, Woodward 505XT, PROTECH GII, SEL-400G, Bently Nevada 3500. Condenser HISTORY: Year Manufactured: 2021/2022 Stored in Warehouse Original Factory Shipping Crates
Location: North America
Used 10 MW Triveni (India) Steam Turbine Generator Set, new in 2008. Consisting of: - Triveni model Frame13ER bleed-condensing steam turbine, new in 2008, has power 10000 kW, inlet steam flow 49.7 tph at steam pressure 64 ata @ 485 Deg.C., includes gearbox Triveni, new in 2008, coupled on common baseframe, input speed 7556 rpm and rate 5.037/1 which gives output speed 1500 rpm, - TDPS type TC145 alternator, new in 2008, capacity 12500 kVA voltage 11000V 3phases 50Hz, - Control system with Woodward TG-17E actuator and interconnected pipings/ cablings, etc - Oil cooling system including tank, centrifuge, pumps, coolers, filters, valves and interconnecting oil pipeline - Сondensing system including condenser with its mountings, inlet and outlet water pipelines, assembly, etc. - Local controls, valves, piping, manuals etc. Reportedly slightly used. More details upon request.
Used SIEMENS type KKK CA-36 condensing turbogenerator set with 15000 hours of operation. Designed electrical output 1800KW. Steam pressure 24.5bar, temperature 430*C, extraction steam pressure 2.1bar, condensing steam pressure 0.1bar. Steam flow 9.5ton/hour. Generator AEM type SE500 M4, Apparent power 2250kVA, 1500rpm, active power 1800KW, 400V, 50Hz. Unit is dismantled and preserved. More information on request.
Stock #V813-204 Sold
Used General Electric (GE) 15000 kW steam turbine-generator Extracting/condensing unit #4. Turbine (no.197858): rating - 15000 kW 3600 rpm, 13 stages, steam CONDITIONS -425PSIG, temperature-740F, exhaust pressure-3,00HG.ABS. Generator air cooled (no.316X400) 2 poles, 3 phase WYE CONN., 60 hertz rating - 24500 kVA, Armature amps-1,025, Armature volts - 13800, field amps-203, excitation volts - 250, power factor - 0,80 inlet water -95F. Generator was under major overhauling in January 2016. Spare parts available.
Location: Western USA
Stock #V813-205 Sold
Used 20 MW Mitsubishi extracting / condensing turbogenerator #5. Meiden synchronous generator type ZIC-aft with output 18941 kVA, 1500 V 60 Hz could extract 425 psi to 150 psi, 1800 rpm, S/N 8N5596P1. Power factor-85%. Spares available. New 2000.
Stock #AG60914 Sold
Used condensing turbo generator Siemens with the capacity 6500kw. Main parameters of the turbo generator: nominal capacity 6500kW. Steam flow 30-35 t/hour. Steam pressure 26 bar. Steam temperature 350°C. Exhaust pressure 0.25bar. Generator Siemens: Voltage 6600 V. 50 hz, 713 A, 8.150 kva, S1, cos 0.8. Gear box Renk, type and size 560, ratio 6.423, speed input 9635 rpm, output 1500 rpm.
Stock #AS60994 Sold
Used 2500 KW twin condensing turbogenerator with extraction. Inlet steam parameters are 41 bar , 400C , 14 t/h. Generator water cooled 6,6 kV, 50Hz, 3,540 kVA (cos fi 0,8). Extraction capacity is 13-14 t/h. Extraction parameters: Temperature, nominal 179 °C, maximal 329 °C. Pressure, nominal 1,9 bar , maximal 3 bar. Steam pressure at the exit 0,2 bar. Main parts of the supply: Turbine by KKK (Siemens) type CFR3/AFA6 GTA. Generator by AvK, Clutch by Renk. oil tank and oil pumps. generator cooler. control panel. Stem condenser is not available.
Stock #AS60995 Sold
Used condensing Siemens Turbine Generator with capacity 10 MW. Main equipment: Condensing Steam Turbine Siemens, 42 t/h, 64 bar, 480°C. Steam extraction 5.3 t/h, 4.4 bar, 207°C. Generator TDPS, 10 000 KW, 11 000 V, 656 A, 50 Hz, 1500 RPM. Gearbox with 5:1 ratio, input 7500 rpm, output 1500 rpm. Condenser Siemens (tube heat exchanger) Controls, Piping, Couplings, Valves, etc. are also included into supply. More information on request.
Used condensing steam turbine generator Dresser Rand type 4QHBT2VIXI, 11,4 MW, 39.5 bar, 390 deg С
Stock #AS60911 Sold
Used condensing steam turbine generator set Dresser Rand type 4QHBT2VIXI with the nominal electrical output 11400 KW. Working steam parameters: 39.5 bar, 390 deg С. Maximum steam parameters: 43 bar, 420 deg C. Steam pressure on the outlet 0.15 -0.2 bar. Generator Jemont type JISALT 412, 15000 kVA, 11000 V. Supply includes: Oil hydraulic station with the heat exchanger. Air-cooled steam condenser by Hamon with the steam pipeline and drainage units. Vacuum condenser. Cooling system. Feed pumps. Control cabinets. New controls.